The module starts and stops the generator, and at the same time indicates the operation status and fault conditions,
If it senses a fault it will automatically shuts down the engine and indicates the engine failure by means of the display panel.
The technician can program the module according to different generator requirements complying with different conditions and protections.
Engine fail to start reattempt:
Engine tries 3 times to start
Engine High Water temperature Protection:
Shutdown activated after 3 sec delay by N/O contacts
Engine Low Oil Pressure Protection:
Shutdown activated after 3 seconds,
Oil Pressure Switch switchable to N/O or N/C sender type.
Engine Over-speed Protection
Shutdown activated after 6 seconds,
50Hz is activated at 55 Hz, 60Hz is activated at 66 Hz
Engine Under Speed Protection:
Shutdown activated after 5 seconds,
50Hz is activated at 45 Hz, 60Hz is activated at 56 Hz
Shutdown activated by NO. Contacts
Spare / User define Shutdown:
Shutdown activated after 5 sec delay by NO. Contacts
Low Battery Voltage Warning:
Activated after 5 seconds delay
12VDC activated at 10VDC, 24VDC activated at 20DCV
Via the front panel.
22 March 2019. Pricing is valid for 30 days, upon print of this page as proof.